Explosion-Proof Pipeline Fire Arrestor
Fire Arrestor is a protective device which use as prevent inflammable gas,fluid's flame spread and avoid temperimg cause to explosion,usually use at beloww conditions:
1.Transport inflammable gas and flammable gas pipelie;
2.Storage petroleum and petroleum product tank;
3.With explosion insecure system vent-pipe;
4.Oil and gas recycling system;
5.Regenerative bolier burning gas pileline net;
6.Gas engine exhaust system;
Main technology parameter
Use as storage flash point lower than 60ºC petrochemical product,such as Gasoline ,kerosene,light diesel oil,toluene etc.
Body material:carbon steel,aluminum alloy,stainless steel:SUS304,SUS304L,SUS316,SUS316L.
Arrestor core material:stainless steel corrugated sheet.
Working pressure:0.6Mpa-5.0Mpa,high pressure should decide by customer.
Maintenance and servicing
^Fire arrestor should check every half of a year,check the flame retardant layer core whether block,deformation,corrosion etc.
^When find block flame retardant layer core should clean,insure every hole in core are unobstructed,should change the deformation,corrosion flame retardant layer.
^Re install the fire resistant layer core parts,should ensure that the combination of surface close not leak.
Previous: No Information